In the next few years new approaches and expansion options are needed for the cleaning of waste water in municipal waste water plants.
The demographic change in cities and municipalities and the related urban expansion will make expansion of many waste water plants necessary. However this will be problematic for many waste water plants in terms of available space.
Multiple studies of discharge outlets of waste water plants have also shown in the last few years that many municipal waste waters are contaminated with micropollutants and trace elements. These include tiny plastic particles from car tires or packaging and anthropogenic residues such as medication, X-ray contrast medium, biocides as well as multiresistant pathogens. These substances are found at the outlet of waste water plants because at many sites the biological cleaning stage is unable to remove all potential contaminants. Therefore the focus turns to the discussion about the so-called 4th cleaning stage at waste water plants.
TDL Energie can offer cost-efficient and space-saving solutions for the new challenges mentioned above.
A procedure to eliminate trace elements that is well-tried in pilot projects uses an additional filtration stage, for example granulated activated carbon in combination with a sandfilter in the outlet of the plant. This technology can be combined with an ozonation installed upstream of the filter which first breaks down the contaminants into low-molecular compounds. These compounds can later be adsorbed by the activated carbon, which is regenerated after reaching complete load capacity. Elimination rates of up to 90 % for medication can be achieved.
However, ozonation is not suitable for particularly contaminated industrial waste waters since ecotoxic byproducts may develop. If the water contains high bromide levels, for exampe, the risk increases that a large quantity of the potentially carcinogenic bromate forms. Therefore the particular water must be tested for suitability before ozonation is implemented.
A second approach is the dosing of activated carbon powder upstream of or directly into the aeration tank. Due to the longer retention time of the activated carbon the adsorption time in the circulatory biological system is prolonged and trace elements can be filtered more effectively. This also enables the development of a biofilm on the surface of the activated carbon which outperforms the degradation rate of conventional activated sludge process. It should, however, be taken into consideration that the complete retention of activated carbon powder is not always feasible with sand filters.
To compensate this disadvantage the ACP-technology may be combined with porous membranes, such as microfiltration or ultrafiltration, to so-called membrane bioreactors (ACP-MBR). For this purpose submersible membrane systems are directly lowered into the aeriation tank. Due to the small pore size of the membranes micro plastics and pathogens can be removed.
Only dense membranes, like those used in nanofiltration and reverse osmosis, are able to filter trace elements directly from the waste water without pretreatment. However, the concentrate of the membrane plants must be disposed of separately. Another advantage of this technology is space-saving. The sludge retention enables the operation of the aeriation tanks with higher sludge content and thus saves space within the expansion of the plant technology.
Due to the great experience of TDL Energie we are able to offer cost-efficient, technically optimized solutions which can be adjusted to the specific requirements of individual sites.